00946 DD 125A 3PH AMF - Mains Distribution Auto Mains Failure panel ( AMF ) Automatic changeover panel
2 x 125A 415V 3PH+N+E IP67 appliance inlets + Neons
1 x 125A 415V 3PH+N+E IP67 Panel Socket + Neons
1 x 63A 415V 3PH+N+E IP67 Panel Socket + Neons Protected by 1x 63A C TYPE 4P MCB
1 x 16A 110V IP44 Remote Start
1 x 16A 240V 1PH+N+E IP44 Panel Socket + Neons Protected by 1x 16a 2P 30ma RCBO
AMF panel is the short form of Auto Mains Failure panel. It is sometimes also called an Automatic Transfer Switch. It is normally connected to the generator set to control the generator set function automatically detecting a power cut and causing the generator to start and support the load. It can call the generator set if it detects that the mains power is lost (power cut) or out of preset tolerances (e.g. brownout). When the AMF panel detects that the mains has failed or is outside of tolerance, it will send a start signal to the generator to startup. Once the generator is ready to accept the load, the motorized switches or contactors in the AMF panel will switch the building load from mains supply to generator. When the mains is restored, the opposite will happen. The AMF panel will put the building load back on to the mains supply and then stop the generator (once it has performed its cool down process).